The Abort Station is designed to be wired to the abort terminals of the Agent Release Control Panel (OCI 77301). The device consists of a Zinc Alloy faceplate and a modular switch assembly. It is designed to mount on a standard single gang electrical enclosure.
Releasing Circuit Disable Switch
Releasing Circuit Disable Switch (RCDS) device consists of a Zinc Alloy faceplate, green LED, amber LED and a switch assembly. It is designed to mount on a standard single gang electrical enclosure.
Main Reserve Switch
The “Main” to “Reserve” Switch is used with systems that incorporate main and reserve (back-up) agent storage. The switch have two kinds of dry contact (COM./N.C. and COM./N.O.) switch separately to avoid any interference by different system.
Following a system discharge, reset any field devices. Once all devices are in a stand-by status, the Main-Reserve Switch may be moved to the “Reserve” position. The Control Panel may then be reset to a normal mode for uninterrupted Orient protection. The empty “Main” containers can be removed for recharge. After the containers in the “Main” system have been recharged, the switch may be returned to the “Main” position.
Manual Pull Station
Orient Manual Pull Station is a dual action and constructed of a solid die cast housing and comes in glossy red. The back switch plate is plated steel. The electrical switch is rated for 10 Amps @ 120 VDC normally open contact rating. It is connected via terminal block connections.